Pico can be installed in different ways. Here you will find the most common variants described with their specific requirements.
The Pico has DC fault detection according to IEC62955. To comply with national installation regulations, a type-A serial RCD is required with each Pico to ensure personal safety.
Installation ribbon cable
RCD Type-A 40A without load circuit breaker in serial to each Pico EV-Charger.
Load circuit breaker at the e-mobility outgoing feeder with short-circuit-proof routing is sufficient for selectivity. (Extended documentation)
Connection cable between ribbon cable and ev-charger must comply with the following points:
Shorter then 3m length
Advanced protection against mechanical damage: Protect cable with aluminium pipe.
Do not lead the connecting cable over flammable areas.
The shortcut current must be high enough to make the installed 63A circuit breaker trip. (Test installation)