Pico EV Charger
Maximum charging power 22 kW at 32A three-phase, 7.36 kW at 32A single-phase
Identification Automatic recognition and identification of the car, RFID / NFC reader (JEWEL, MIFARE, FELICA, ISO14443, NFC_DEP, ISO14443_B, ISO15693)
Smart Meter Integrated electricity meter incl. security processor
Phase balancing Automatic phase balancing
Load management Automatic load management via several stations
Cloud connection Connection to smart-me and eCarUp Cloud
Safety Integrated Article number 202170: RDC-DD (20mA AC, 6mA DC), Article number 202170exA: RDC-DD 6mA according to IEC 62955 (Fault DC detection device)
Temperature range -30°C to 50°C
Mains voltages 3x230/400VAC or 1x 230VAC (+/-10%)
Charging socket IEC 62196-2 type 2
Protection class IP55 (indoor and outdoor)
Impact resistance class IK10
Flammability rating UL94
Load shedding 2 potential-free inputs (4 states), min. 12V AC/DC, max. 48 VDC / 230 VAC
S0 output S0 interface (1000 imp/kwh) for calibration
Power connection top, bottom, rear
Installation type Busbar, ribbon cable, star-shaped
Dimensions H:300 mm W:220 mm D:112 mm
Weight 3.8 kg
Cable cross-section min. 2.5 mm2, max. 10 mm2
Cable diameter 10-20 mm
Server location Switzerland
Pico Connectors and Dimensions
L1: Phase 1
L2: Phase 2
L3: Phase 3
N: Neutral conductor / Neutral conductor
PE: Protective earth
The protective earth conductor should be attached to the upper connection screw so that the stand is earthed directly together with the station.
The product can only be operated in 3-phase star connection or 1-phase!
The cables can be fed in and out of Pico at 5 points.
Two at the top, two at the bottom and one through the back plate.
When mounting through the back plate, a hole with a diameter of 25-26mm must be drilled.
Details on mounting the stand can be found in the installation instructions in the downloads.
Load shedding (external inputs)
Load shedding can also be implemented using only one available signal.
For the configuration from no charge to maximum charge power, the signal is wired to IN1 and IN2 as well as COM.
For the configuration from 6A minimum power to maximum charging power, the signal must only be wired to IN2 as well as COM.
The load shedding can either be wired to all Picos or minimally to one from each load group.
This function also works in case of no internet connection.
Alternatively, the load shedding can also be done via the IF/THEN actions and Pico control.